Element | Parameter | Value |
---|---|---|

Gas turbine |
High-pressure firing temperature, TIT_{HP} (K)^{a}
| 1,700 |

Flow rate, m
_{out} (kg/s)
| 685 | |

Power, W
_{s} (MJ/kg)
| 339 | |

Steam turbine |
Specific work, W (kJ/kg)
| 506 |

High pressure, P
_{HP} (bar)^{a}
| 150 | |

Intermediate pressure, P
_{IP,opt} (bar)
| 40 | |

Low pressure, P
_{LP, opt} (bar)
| 3.2 | |

Condensation pressure, P
_{cond} (kPa)^{a}
| 7 | |

Flow rate of high pressure, m
_{HP} (kg/s)
| 101.1 | |

Flow rate of intermediate pressure, m
_{IP} (kg/s)
| 110.7 | |

Flow rate of low pressure, m
_{LP} (kg/s)
| 121.6 | |

Power, W (MW)
| 173 | |

Specific work, W
_{s} (kJ/kg)
| 259 | |

Boiler |
Maximum steam temperature, T
_{max, steam} (K)
| 833 |

Gas temperature at the exit of the HRSG, T
_{out} (K)
| 365 | |

HRSG heat duty (MW) | 410 | |

Overall performances |
CC power, W
_{el} (MW)
| 505 |

CC specific work, W
_{s, el} (kJ/kg)
| 754 | |

CC efficiency, η
_{el} (%)
| 60.1 |